## Column Diameter

Since the pressure drop directly impacts the operating cost for the blower to deliver the feed gas, the design engineer should choose the tower diameter to meet the pressure drop specification. Figure 5.20.3 shows the value for a widely used correlation for the pressure drop calculation. The correlation includes a parameter, packing factor FP, which is a constant for a given packing size and shape (Fair 1987). The value of Fp can be obtained from Table 5.20.2. With known physical properties and flowrates for the liquid and gas streams, the engineer first determines the specific gas rate G, kg/m2 • sec in the column and then calculates the column cross-sectional area by dividing the total gas flowrate (GT,kg/s) by G.

In cases where the pressure drop is not a prime consideration (e.g., treatment of a pressurized process stream), the column can be designed to operate at 70-80% of flooding rate. For packings below 2.5 cm size, the design engineer can use the flooding line shown in Figure 5.20.3 to calculate the flooding rate. If the packing is larger than 3.7 cm, the following empirical equation determines the pressure drop at flooding (McCabe 1993):

## Trash To Cash

This book will surely change your life due to the fact that after reading this book and following through with the steps that are laid out for you in a clear and concise form you will be earning as much as several thousand extra dollars a month,  as you can see by the cover of the book we will be discussing how you can make cash for what is considered trash by many people, these are items that have value to many people that can be sold and help people who need these items most.

Get My Free Ebook